System Grounding. For a photovoltaic power source, one conductor of a two-wire system with a photovoltaic system voltage over 50 volts and the reference (center tap) conductor of a bipolar system shall be solidly grounde3d or shall use other methods that accomplish equivalent system protection in accordance with 250.4(A) and that utilize equipment listed and identified for the use. Exception: Systems complying with 690.35.
Point of System Grounding Connection. The dc circuit grounding connection shall be made at any single point on the photovoltaic output circuit.
Equipment Grounding. Exposed non-current carrying metal parts of module frames, equipment, and conductors enclosures shall be grounded in accordance with 250.134 or 250.136(A) regardless of voltage.
Size of Equipment Grounding Conductor. Where not protected by the ground-fault protection equipment required by 690.5, the equipment-grounding conductor for photovoltaic source and photovoltaic output circuits shall be sized for 125 percent of the photovoltaic-originated short-circuit currents in that circuit. Where protected by the ground-fault protection equipment required by 690.5, the equipment-ground conductors for photovoltaic source and photovoltaic output circuits shall be sized in accordance with 250.122.
Grounding Electrode System.
Alternating-Current Systems. If installing an ac system, a grounding electrode system shall be provided in accordance with 250.50 through 250.60. The grounding electrode conductor shall be installed in accordance with 250.64.
Direct-Current Systems. If installing a dc system, a grounding electrode system shall be provided in accordance with 250.166 for grounded systems or 250.169 for ungrounded systems. The grounding electrode conductor shall be installed in accordance with 250.64. ,br>
Systems with Alternating-Current and Direct-Current Grounding Requirements. Photovoltaic power systems with both alternating-current and direct-current (dc)grounding requirements shall be permitted to be grounded as described bellow:
A grounding-electrode conductor shall be connected between the identified dc grounding point to a separate dc grounding electrode. The dc grounding-electrode to make a grounding electrode system according to 250.52 and 250.53. The bonding conductor shall be no smaller than the largest grounding electrode conductor, either ac or dc.
The dc grounding electrode conductor and ac grounding electrode conductor shall be connected to a single grounding electrode. The separate grounding electrode conductors shall be sized as required by 250.66 (ac) and 250.166 (dc).
Continuity of Equipment Grounding Systems. Where the removal of equipment disconnects the bonding connection between the grounding electrode conductor and exposed conducting surfaces in the photovoltaic source or output circuit equipment, a bonding jumper shall be installed while the equipment is removed.
Continuity of Photovoltaic Source and Output Circuit Grounded Conductors. Where the removal of the utility-interactive inverter or other equipment disconnects the bonding connection between the grounding electrode conductor and the photovoltaic source and/or photovoltaic output circuit grounded conductor, a bonding jumper shall be installed to maintain the system grounding while the inverter or other equipment is removed.
BD Batteries - A Broomfield-Designers Company
Serving the Local Colorado Community 9-5 Mountain & Emergencies P. 303-800-4725 F. 303-600-9726
Serving the Buffalo and the Great Lakes Communities 9-5 Eastern & Emergencies P. 716-531-4875
Mailing Address: 5023 West 120th Ave. #138, Broomfield, CO 80020
OUR DENVER WAREHOUSE IS MOVING TO A NEW LOCATION AT THIS TIME.
WE WERE SCHEDULED TO REOPEN OUR BRICK AND MORTAR BATTERY WAREHOUSE IN EARLY 2011.
IN THE MEAN TIME OUR WEBSITE AND PHONES OPERATE FINE!
We do thank the public for the outreach of concern, and votes of confidence.
Do call Lorene prior to schedule used battery pickups, new battery dropoffs, etc. by appointment.
The information contain on this deep cycle AGM batteries website is deemed reliable, but not guaranteed. Please verify specific information on marine AGM batteries, rv AGM batteries or auto AGM batteries listed here by calling us direct. We are proud to offer the highest quality AGM batteries and hope you will consider using our deep cycle AGM batteries in the near future!